180 Wall-Mount PIR Motion Sensor Switch with Light Sensor, Energy Saving Sensor,LUX Adjustment, Time Adjustment,Automatic Sensor
This product is a new type of energy-saving lighting switch, it adopts a high sensitivity detector, integrates circuits, and SMT. It gathers automatic, convenient, safe,energy-saving, practical functions. It has a wide detection range made up of up and down, left and right service fields. It utilizes human motion infrared rays as control signal sources, when one enters the detection field, it will start the controlled load at once. It can identify day and night automatically. It is easy to install and its usage is wide. It has the function of power indication and detection indication.
Detection field: The wide detection range is made up of up and down, left and right(see the following diagram), the detection range could be adjusted according to your desire, but the moving orientation in the detection field has great relation with the sensitivity.
Identify day and night automatically: The light-control of it could be adjusted according to your desire. when turning to SUN (max), it will work day and night, when turning it to MOON (min), it will only work in the light-control less than 3LUX As for adjustment, please refer to testing way.
Time delay is added continually: When it receives the second induction signals after the first induction, it will compute time once more on the rest of the first time-delay basis (set time). Time delay is adjustable. It can be set according to your desire, the minimum is 8s±3s, the maximum, the maximum is 7min±2min.
Shut off the power.
Loosen the screw on the bottom lid. open the wining hole, pass the wire of power, and load through the bottom lid.
Fix the bottom lid with an inflated screw on the selected position.
Connect the power and load wire into the connection-wire column.
Put the sensor on the bottom lid, twist the screw tightly then electrify it and test it.
Turn the light-control knob clockwise to the maximum (SUN), turn the time knob anti-clockwise to the minimum. Switch on power, the controlled load should not work, under the no induction signal condition, the load should stop work within 5-30sec. Make it sense again 5-10sec later since the first is out, the load should work, the load should stop working within 5-20sec. Turn the LUX knob to minimum anti-clockwise, if you test it when the light control is more than 3LUXx, the induction load would not work after the load stops working. the load should work if you cover the detection window with an opaque object (towel etc). It would be regular the load stops to work within 5-15sec under no induction signal condition.
|Power Sourcing||220V-240V AC|
|Working Temperature||-10° to 40° C|
|Ambient Light||<3 LUX (Adjustable)|
|Time-Delay||min. 8sec±3sec and Max. 8mint±2min|
|Power Consumption||0.45W (work) and 0.1W (static)|
|Rated Load||1200W Max. Tungsten and 300W Max. Fluorescent|
|Detection Motion Speed||0.6-1.5m/s|
|Detection Distance||12m max (<24° C)|